This is an insulation test of motor windings, commonly referred to as megging, to megger, or to meg a motor. We are testing the motor’s insulation, more specifically between the motor windings and the motor casing. … Using a megohmmeter properly will test any motor insulation.
Why do you meg a motor?
Megger testing measures resistance between the phase windings of the motor under test and ground. If there is an insulation breakdown, the resistance is negatively impacted and there is a departure between phases or between one measurement and a previous one and a determination of motor health is made.
What is a bad Megger reading on a motor?
What is a bad reading on a Megger test? If the megger reads a resistance under 1 (1,000 ohms) on your meter after the initial 60-second interval, the cable has failed and the cable should be removed. If the megger reads a resistance between 1-1.25 on your meter, then the cable passes.
What is a good megohm reading for a motor?
Insulation resistance should be approximately one megohm for each 1,000 volts of operating voltage, with a minimum value of one megohm. For example, a motor rated at 2,400 volts should have a minimum insulation resistance of 2.4 megohms.
Can a megger damage a motor?
Never use a megger if the motor windings are under a vacuum. … A high voltage for too long of a time may further weaken or fail motor windings and the winding insulation could be damaged by the testing procedure.
How much resistance should a motor have?
Earth Continuity and Resistance Test
A good motor should read less than 0.5 ohms. Any value greater 0.5 ohms indicate trouble with the motor.
How do you meg a wire?
Clamp the alligator clip on one of the megger probes to the wire or cable, touch the other probe to the exposed conductor and press the test button. The megger will generate a current between the probes, and the meter will record the resistance of the jacket to the flow of the current.
How do you know if a 3 phase motor is bad?
Using a multimeter, check the continuity of motor winding from phase to phase ( U to V, V to W , W to U ). Each phase to phase must have a continuity if winding is OK. If any particular phase fails the continuity test, your motor is probably burnt.
How do I know if my electric motor is bad?
With a multimeter set to low ohms (usually 200), test between each winding terminal and the metal casing of the motor. If there is any reading on any of these then the motor is bad, do not use it. You may find that when it runs ungrounded that the casing becomes live at up to supply voltage.
How do you know if you burned your engine?
You should test the windings for a “short to ground” in the circuit and open or shorts in the windings. To test your motor for short to ground, you’ll need to set the multimeter to ohms and disconnect the motor from its power source. Then inspect each wire and look for infinite readings.
What does a reading of 0 ohms mean?
Ohms is a measurement of resistance so “zero ohms” means no resistance. All conductors offer some resistance, so technically, there is no such thing as zero ohms.
What is a bad insulation resistance reading?
The purpose of the IR test is to check for damaged insulation, this can be mechanical damage or damage by heat, (overloaded cables), readings less than 2 Mohm indicate damaged insulation, readings of 2-50 Mohm are indicative of long circuit lengths, moisture and contamination and do not indicate the insulation quality, …
What is the minimum insulation resistance of a motor?
It is recommended that the insulation resistance of the motor should at least be 1 MΩ1）, and for the voltage to ground of 200 V, I0r should be 200 μA or below.